Simple introduction and selection of power inverter
Sourc:The SiteAddtime:2017/10/24 Click:0
The power inverter is a backup uninterruptible power supply. AC
high-speed conversion, which is mainly completed by the DC to AC
inverter, as well as the exchange of electricity and inverter high-speed
conversion. Usually can be set according to the application of DC main or AC main use, by the static switch control high-speed switching.
The main internal structure of the power inverter is as follows:
Filter section: input filter for the input DC power supply noise filter, get a smooth DC, into the inverter. The output filter filters out the output harmonics and disturbances, making the output smoother.
Inverter: convert DC power to sinusoidal AC power.
Control part: control the inverter power supply to follow the base
power, and keep the same phase and frequency, automatic adjustment, and
the power within the specified range, in accordance with the set value
of protection operation or protection.
Display part: LCD and LED status simulation disk, accurately reflect the equipment running status and fault information.
Switching part: automatic switching of bypass, mains and inverter output power.
The structure of the power inverter is as follows:
Rack type: also known as drawer, easy to install and wiring cabinet;
group cabinet installation more beautiful, more coordinated.
Vertical: also known as floor type.
Power inverter and ordinary UPS power supply difference and advantages:
use of power plants or substations existing DC screen, installed power
UPS or power inverter power supply uninterruptible power supply, than
the conventional UPS has many advantages. "Reliable DC + Reliable Inverter", can provide more efficient and longer protection for the equipment.
DC terminal 220VDC / DC110V design (according to the existing DC screen
or battery voltage level setting), you can use the substation or
communication base station existing DC battery, you can save investment
and greatly extend the standby time. Avoid duplication of investment.
2> Due to the above environment, the battery pack has a professional maintenance, life can be greatly extended.
3> with RS232 / RS485 communication interface to facilitate the background monitoring equipment working status.
4> rack design, easy to install cabinet
5> load capacity, can adapt to a wider load demand, voltage and output waveform more stable.
Power inverter product selection Note:
to determine whether the power-specific, power-specific power inverter,
the internal structure containing DC / DC isolation, supporting the use
of DC power supply, more secure and reliable. If a normal inverter changes the product, there may be a risk of
electrical counter-irrigation, electrical damage to the appliance, or
2: Determine the actual size of the load, select the appropriate power inverter. Because
if the selection is too large, investment waste; and power selection is
too small, may be carrying capacity is not enough, lead the power
inverter overload protection phenomenon. Therefore,
the choice of power inverter, you should first determine the maximum
impact power load, in particular, to consider the load inductive load,
because the emotional load in the boot moment several times the impact
of amplification. The actual power of the power inverter should be greater than the sum of the maximum power of all loads.
3: determine the required power inverter shape, DC voltage, product color, communication interface and other factors.
Ouli Electric professional production of power inverter and other power
products, more than 10 years of professional production and use of
experience, the details of the company can be linked with the sales
manager consulting, will be the greatest enthusiasm and the most
professional to help users selection product.